012701 DILEM4G(24VDC)
Contactor, 24 V DC, 4 pole, 380 V 400 V, 4 kW, Screw terminals, DC operation
Alternate Catalog No.
XTMF9A00TD
Contactor, Application: Mini Contactors for Motors and Resistive Loads, DILEM contactors, Utilization category: AC1: Noninductive or slightly inductive loads, resistance furnaces, NAC3: Normal AC induction motors: starting, switch off during running, AC4: Normal AC induction motors: starting, plugging, reversing, inching, Connection technique: Screw terminals, Number of poles: 4 pole, Rated operational current AC3 380 V 400 V: Ie= 9 A, Rated operational current AC1 Conventional free air thermal current, 3 pole, 50  60 Hz Open at 40 °C: Ith =Ie= 22 A, enclosed: Ith= 16 A, Rated operational current AC1 Conventional free air thermal current, 1 pole open: Ith= 60 A, enclosed: Ith= 50 A, Max. rating for threephase motors, 50  60 Hz AC3 220 V 230 V: P= 2.2 kW, 380 V 400 V: P= 4 kW, 660 V 690 V: P= 4 kW, Max. rating for threephase motors, 50  60 Hz AC4 220 V 230 V: P= 1.5 kW, 380 V 400 V: P= 3 kW, 660 V 690 V: P= 3 kW, For use with: …DILEM, …DILE, Voltage AC/DC: DC operation
Delivery program
Product range
Contactors
Application
Mini Contactors for Motors and Resistive Loads
Subrange
DILEM contactors
Utilization category
AC1: Noninductive or slightly inductive loads, resistance furnaces
NAC3: Normal AC induction motors: starting, switch off during running
AC4: Normal AC induction motors: starting, plugging, reversing, inching
NAC3: Normal AC induction motors: starting, switch off during running
AC4: Normal AC induction motors: starting, plugging, reversing, inching
Connection technique
Screw terminals
Number of poles
4 pole
Rated operational current
AC3380 V 400 V [I_{e}]
9 A
AC1Conventional free air thermal current, 3 pole, 50  60 HzOpenat 40 °C [I_{th }=I_{e}]
22 A
Max. rating for threephase motors, 50  60 Hz
AC3220 V 230 V [P]
2.2 kW
AC3380 V 400 V [P]
4 kW
AC3660 V 690 V [P]
4 kW
AC4220 V 230 V [P]
1.5 kW
AC4380 V 400 V [P]
3 kW
AC4660 V 690 V [P]
3 kW
Instructions
Integrated dioderesistor combination
For use with
…DILEM
…DILE
…DILE
Actuating voltage
24 V DC
Voltage AC/DC
DC operation
Technical data
General
Standards
IEC/EN 60947, VDE 0660, CSA, UL
Lifespan, mechanical [Operations]
20 x 10^{6}
Maximum operating frequencyMechanical
9000 Ops./h
Maximum operating frequencyelectrical (Contactors without overload relay) [Operations/h]
Page 05/070
Climatic proofing
Damp heat, constant, to IEC 60068278
Damp heat, cyclic, to IEC 60068230
Damp heat, cyclic, to IEC 60068230
Ambient temperatureOpen
25  +50 °C
Ambient temperatureEnclosed
 25  40 °C
Ambient temperatureStorageMin. ambient temperature, storage
 40 °C
Ambient temperatureStorageAmbient temperature, storage max.
+ 80 °C
Mounting position
As required, except vertical with terminals A1/A2 at the bottom
Mechanical shock resistance (IEC/EN 60068227)Halfsinusoidal shock, 10 msBasic unit without auxiliary contact moduleMain contacts, make contacts
10 g
Mechanical shock resistance (IEC/EN 60068227)Halfsinusoidal shock, 10 msBasic unit with auxiliary contact moduleMain contacts make contactMake
10 g
Mechanical shock resistance (IEC/EN 60068227)Halfsinusoidal shock, 10 msBasic unit with auxiliary contact moduleAuxiliary contacts Make/break contacts
20/20 g
Degree of Protection
IP20
Protection against direct contact when actuated from front (EN 50274)
Finger and backofhand proof
Altitude
Max. 2000 m
Weight
0.206 kg
Terminal capacity of auxiliary and main contactsScrew terminalsSolid
1 x (0.75  2.5)
2 x (0.75  2.5) mm^{2}
2 x (0.75  2.5) mm^{2}
Terminal capacity of auxiliary and main contactsScrew terminalsFlexible with ferrule
1 x (0.75  1.5)
2 x (0.75  1.5) mm^{2}
2 x (0.75  1.5) mm^{2}
Terminal capacity of auxiliary and main contactsScrew terminalsSolid or stranded
18  14 AWG
Terminal capacity of auxiliary and main contactsScrew terminalsStripping length
8 mm
Terminal capacity of auxiliary and main contactsScrew terminalsTerminal screw
M3.5
Terminal capacity of auxiliary and main contactsScrew terminalsPozidriv screwdriver
2 Size
Terminal capacity of auxiliary and main contactsScrew terminalsStandard screwdriver
0.8 x 5.5
1 x 6 mm
1 x 6 mm
Terminal capacity of auxiliary and main contactsScrew terminalsMax. tightening torque
1.2 Nm
Main conducting paths
Rated impulse withstand voltage [U_{imp}]
6000 V AC
Overvoltage category/pollution degree
III/3
Rated insulation voltage [U_{i}]
690 V AC
Rated operational voltage [U_{e}]
690 V AC
Safe isolation to EN 61140between coil and contacts
300 V AC
Safe isolation to EN 61140between the contacts
300 V AC
Making capacity (cos ϕ to IEC/EN 60947)
90 A
Breaking capacity 220 V 230 V
90 A
Breaking capacity 380 V 400 V
90 A
Breaking capacity 500 V
64 A
Breaking capacity 660 V 690 V
42 A
Shortcircuit protection maximum fuseType ”2”, 500 V [gL/gG]
10 A
Shortcircuit protection maximum fuseType ”1”, 500 V [gL/gG]
20 A
AC
AC1Rated operational currentConventional free air thermal current, 3 pole, 50  60 HzOpenat 40 °C [I_{th }=I_{e}]
22 A
AC1Rated operational currentConventional free air thermal current, 3 pole, 50  60 HzOpenat 50 °C [I_{th }=I_{e}]
20 A
AC1Rated operational currentConventional free air thermal current, 3 pole, 50  60 HzOpenat 55 °C [I_{th }=I_{e}]
19 A
AC1Rated operational currentConventional free air thermal current, 3 pole, 50  60 Hzenclosed [I_{th}
]
16 A
AC1Rated operational currentConventional free air thermal current, 3 pole, 50  60 HzNotes
At maximum permissible ambient air temperature.
AC1Rated operational currentConventional free air thermal current, 1 poleNotes
At maximum permissible ambient air temperature.
AC1Rated operational currentConventional free air thermal current, 1 poleopen [I_{th}
]
60 A
AC1Rated operational currentConventional free air thermal current, 1 poleenclosed [I_{th}
]
50 A
AC3Rated operational currentOpen, 3pole: 50 – 60 HzNotes
At maximum permissible ambient temperature (open.)
AC3Rated operational currentOpen, 3pole: 50 – 60 Hz220 V 230 V [I_{e}]
9 A
AC3Rated operational currentOpen, 3pole: 50 – 60 Hz240 V [I_{e}]
9 A
AC3Rated operational currentOpen, 3pole: 50 – 60 Hz380 V 400 V [I_{e}]
9 A
AC3Rated operational currentOpen, 3pole: 50 – 60 Hz415 V [I_{e}]
9 A
AC3Rated operational currentOpen, 3pole: 50 – 60 Hz440V [I_{e}]
9 A
AC3Rated operational currentOpen, 3pole: 50 – 60 Hz500 V [I_{e}]
6.4 A
AC3Rated operational currentOpen, 3pole: 50 – 60 Hz660 V 690 V [I_{e}]
4.8 A
AC3Motor rating [P]220 V 230 V [P]
2.2 kW
AC3Motor rating [P]240V [P]
2.5 kW
AC3Motor rating [P]380 V 400 V [P]
4 kW
AC3Motor rating [P]415 V [P]
4.3 kW
AC3Motor rating [P]440 V [P]
4.6 kW
AC3Motor rating [P]500 V [P]
4 kW
AC3Motor rating [P]660 V 690 V [P]
4 kW
AC4Rated operational currentOpen, 3pole: 50 – 60 HzNotes
At maximum permissible ambient air temperature.
AC4Rated operational currentOpen, 3pole: 50 – 60 Hz220 V 230 V [I_{e}
]
6.6 A
AC4Rated operational currentOpen, 3pole: 50 – 60 Hz240 V [I_{e}
]
6.6 A
AC4Rated operational currentOpen, 3pole: 50 – 60 Hz380 V 400 V [I_{e}
]
6.6 A
AC4Rated operational currentOpen, 3pole: 50 – 60 Hz415 V [I_{e}
]
6.6 A
AC4Rated operational currentOpen, 3pole: 50 – 60 Hz440 V [I_{e}
]
6.6 A
AC4Rated operational currentOpen, 3pole: 50 – 60 Hz500 V [I_{e}
]
5 A
AC4Rated operational currentOpen, 3pole: 50 – 60 Hz660 V 690 V [I_{e}
]
3.4 A
AC4Motor rating [P]220 V 230 V [P]
1.5 kW
AC4Motor rating [P]240 V [P]
1.8 kW
AC4Motor rating [P]380 V 400 V [P]
3 kW
AC4Motor rating [P]415 V [P]
3.1 kW
AC4Motor rating [P]440 V [P]
3.3 kW
AC4Motor rating [P]500 V [P]
3 kW
AC4Motor rating [P]660 V 690 V [P]
3 kW
DC
Rated operational current openDC112 V [I_{e}
]
20 A
Rated operational current openDC124 V [I_{e}
]
20 A
Rated operational current openDC160 V [I_{e}
]
20 A
Rated operational current openDC1110 V [I_{e}
]
20 A
Rated operational current openDC1220 V [I_{e}
]
20 A
Current heat losses (3 or 4pole)at I_{th}, 50 °C
5.9 W
Magnet systems
Voltage toleranceDC operatedPickup voltage
0.85  1.1
Power consumptionDC operationPower consumption Pickup = Sealing
2.3 VA/W
Power consumptionDC operationNotes
Smoothed DC voltage or threephase bridge rectifier
Duty factor
100 % DF
Switching times at 100 % U_{c}Make contactClosing delayClosing delay min.
26 ms
Switching times at 100 % U_{c}Make contactClosing delayClosing delay max.
35 ms
Switching times at 100 % U_{c}Make contactOpening delayOpening delay min.
15 ms
Switching times at 100 % U_{c}Make contactOpening delayOpening delay max.
25 ms
Switching times at 100 % U_{c}Make contactClosing delay with top mounting auxiliary contact
70 ms
Switching times at 100 % U_{c}Reversing contactorsChangeover time at 110 % U_{c}Changeover time min.
40 ms
Switching times at 100 % U_{c}Reversing contactorsChangeover time at 110 % U_{c}Changeover time max.
50 ms
Switching times at 100 % U_{c}Reversing contactorsArcing time at 690 V AC
12 ms
Auxiliary contacts
Positive operating contacts to EN 6094751 appendix L, including auxiliary contact module
Yes
Rated impulse withstand voltage [U_{imp}
]
6000 V AC
Overvoltage category/pollution degree
III/3
Rated insulation voltage [U_{i}
]
690 V AC
Rated operational voltage [U_{e}
]
600 V AC
Safe isolation to EN 61140between coil and auxiliary contacts
300 V AC
Safe isolation to EN 61140between the auxiliary contacts
300 V AC
Rated operational currentAC15220 V 240 V [I_{e}]
6 A
Rated operational currentAC15380 V 415 V [I_{e}]
3 A
Rated operational currentAC15500 V [I_{e}]
1.5 A
Rated operational currentDC L/R ≦ 15 msContacts in series:1 [24 V]
2.5 A
Rated operational currentDC L/R ≦ 15 msContacts in series:2 [60 V]
2.5 A
Rated operational currentDC L/R ≦ 15 msContacts in series:3 [100 V]
1.5 A
Rated operational currentDC L/R ≦ 15 msContacts in series:3 [220 V]
0.5 A
Conv. thermal current [I_{th}]
10 A
Control circuit reliability [Failure rate]
<10^{8}, < one failure at 100 million operations
(at U_{e} = 24 V DC, U_{min} = 17 V, I_{min} = 5.4 mA) λ
(at U_{e} = 24 V DC, U_{min} = 17 V, I_{min} = 5.4 mA) λ
Component lifespan at U_{e} = 240 VAC15 [Operations]
0.2 x 10^{6}
Component lifespan at U_{e} = 240 VDC currentL/R = 50 ms: 2 contacts in series at I_{e} = 0.5 A [Operations]
0.15 x 10^{6}
Component lifespan at U_{e} = 240 VDC currentNotes
Switchon and switchoff conditions based on DC13, time constant as specified
Shortcircuit rating without weldingMaximum overcurrent protective deviceShortcircuit protection only
PKZM04
Shortcircuit rating without weldingShortcircuit protection maximum fuse500 V
6 A gG/gL
Shortcircuit rating without weldingShortcircuit protection maximum fuse500 V
10 A fast
Current heat loss at a load of I_{th} per contact
1.1 W
Rating data for approved types
Switching capacityMaximum motor ratingThreephase200 V
208 V
208 V
2 HP
Switching capacityMaximum motor ratingThreephase230 V
240 V
240 V
3 HP
Switching capacityMaximum motor ratingThreephase460 V
480 V
480 V
5 HP
Switching capacityMaximum motor ratingThreephase575 V
600 V
600 V
5 HP
Switching capacityMaximum motor ratingSinglephase115 V
120 V
120 V
0.5 HP
Switching capacityMaximum motor ratingSinglephase230 V
240 V
240 V
1.5 HP
Switching capacityGeneral use
15 A
Short Circuit Current RatingBasic RatingSCCR
5 kA
Short Circuit Current RatingBasic Ratingmax. Fuse
45 A
Design verification as per IEC/EN 61439
Technical data for design verification
Rated operational current for specified heat dissipation [I_{n}]
22 A
Heat dissipation per pole, currentdependent [P_{vid}]
1.79 W
Equipment heat dissipation, currentdependent [P_{vid}]
7.17 W
Static heat dissipation, noncurrentdependent [P_{vs}]
2.3 W
Heat dissipation capacity [P_{diss}]
0 W
Operating ambient temperature min.
25 °C
Operating ambient temperature max.
+50 °C
IEC/EN 61439 design verification
10.2 Strength of materials and parts10.2.2 Corrosion resistance
Meets the product standard's requirements.
10.2 Strength of materials and parts10.2.3.1 Verification of thermal stability of enclosures
Meets the product standard's requirements.
10.2 Strength of materials and parts10.2.3.2 Verification of resistance of insulating materials to normal heat
Meets the product standard's requirements.
10.2 Strength of materials and parts10.2.3.3 Verification of resistance of insulating materials to abnormal heat and fire due to internal electric effects
Meets the product standard's requirements.
10.2 Strength of materials and parts10.2.4 Resistance to ultraviolet (UV) radiation
Meets the product standard's requirements.
10.2 Strength of materials and parts10.2.5 Lifting
Does not apply, since the entire switchgear needs to be evaluated.
10.2 Strength of materials and parts10.2.6 Mechanical impact
Does not apply, since the entire switchgear needs to be evaluated.
10.2 Strength of materials and parts10.2.7 Inscriptions
Meets the product standard's requirements.
10.3 Degree of protection of ASSEMBLIES
Does not apply, since the entire switchgear needs to be evaluated.
10.4 Clearances and creepage distances
Meets the product standard's requirements.
10.5 Protection against electric shock
Does not apply, since the entire switchgear needs to be evaluated.
10.6 Incorporation of switching devices and components
Does not apply, since the entire switchgear needs to be evaluated.
10.7 Internal electrical circuits and connections
Is the panel builder's responsibility.
10.8 Connections for external conductors
Is the panel builder's responsibility.
10.9 Insulation properties10.9.2 Powerfrequency electric strength
Is the panel builder's responsibility.
10.9 Insulation properties10.9.3 Impulse withstand voltage
Is the panel builder's responsibility.
10.9 Insulation properties10.9.4 Testing of enclosures made of insulating material
Is the panel builder's responsibility.
10.10 Temperature rise
The panel builder is responsible for the temperature rise calculation. Eaton will provide heat dissipation data for the devices.
10.11 Shortcircuit rating
Is the panel builder's responsibility. The specifications for the switchgear must be observed.
10.12 Electromagnetic compatibility
Is the panel builder's responsibility. The specifications for the switchgear must be observed.
10.13 Mechanical function
The device meets the requirements, provided the information in the instruction leaflet (IL) is observed.
Technical data ETIM 7.0
Lowvoltage industrial components (EG000017) / Power contactor, AC switching (EC000066)
Electric engineering, automation, process control engineering / Lowvoltage switch technology / Contactor (LV) / Power contactor, AC switching (ecl@ss10.0.127371003 [AAB718015])
Rated control supply voltage Us at AC 50HZ
0  0 V
Rated control supply voltage Us at AC 60HZ
0  0 V
Rated control supply voltage Us at DC
24  24 V
Voltage type for actuating
DC
Rated operation current Ie at AC1, 400 V
22 A
Rated operation current Ie at AC3, 400 V
9 A
Rated operation power at AC3, 400 V
4 kW
Rated operation current Ie at AC4, 400 V
6.6 A
Rated operation power at AC4, 400 V
3 kW
Rated operation power NEMA
3.7 kW
Modular version
No
Number of auxiliary contacts as normally open contact
0
Number of auxiliary contacts as normally closed contact
0
Type of electrical connection of main circuit
Screw connection
Number of normally closed contacts as main contact
0
Number of main contacts as normally open contact
4
Approvals
Product Standards
IEC/EN 6094741; UL 508; CSAC22.2 No. 1405; CE marking
UL File No.
E29096
UL Category Control No.
NLDX
CSA File No.
012528
CSA Class No.
321104
North America Certification
UL listed, CSA certified
Specially designed for North America
No
Characteristics
Accessories
1: Overload relay
2: Suppressor
3: Auxiliary contact modules
Enclosure totally insulated
2: Suppressor
3: Auxiliary contact modules
Enclosure totally insulated
Squirrelcage motor
Operating characteristics
Starting:from rest
Stopping:after attaining full running speed
Electrical characteristics
Make: up to 6 x rated motor current
Break: up to 1 x rated motor current
Utilization category
100 % AC3
Typical applications
Compressors
Lifts
Mixers
Pumps
Escalators
Agitators
Fans
Conveyor belts
Centrifuges
Hinged flaps
Bucketelevators
Air conditioning system
General drives in manufacturing and processing machines
Operating characteristics
Starting:from rest
Stopping:after attaining full running speed
Electrical characteristics
Make: up to 6 x rated motor current
Break: up to 1 x rated motor current
Utilization category
100 % AC3
Typical applications
Compressors
Lifts
Mixers
Pumps
Escalators
Agitators
Fans
Conveyor belts
Centrifuges
Hinged flaps
Bucketelevators
Air conditioning system
General drives in manufacturing and processing machines
Extreme switching duty
Squirrelcage motor
Operating characteristics
Inching, plugging, reversing
Electrical characteristics
Make: up to 6 x rated motor current
Break: up to 6 x rated motor current
Utilization category
100 % AC4
Typical applications
Printing presses
Wiredrawing machines
Centrifuges
Special drives for manufacturing and processing machines
Squirrelcage motor
Operating characteristics
Inching, plugging, reversing
Electrical characteristics
Make: up to 6 x rated motor current
Break: up to 6 x rated motor current
Utilization category
100 % AC4
Typical applications
Printing presses
Wiredrawing machines
Centrifuges
Special drives for manufacturing and processing machines
Switching duty for nonmotor loads, 3pole, 4pole
Operating characteristics
Noninductive or slightly inductive loads
Electrical characteristics
Make: 1 x rated current
Break: 1 x rated current
Utilization category
100 % AC1
Typical applications
Electric heat
Operating characteristics
Noninductive or slightly inductive loads
Electrical characteristics
Make: 1 x rated current
Break: 1 x rated current
Utilization category
100 % AC1
Typical applications
Electric heat
Shorttime loading, 3pole
Time interval between two loading cycles: 15 minutes
Time interval between two loading cycles: 15 minutes

(Web)

Eaton EMEA DownloadCenter  download data for this item

Eaton EMEA DownloadCenter