010086 DILEM01(24V50HZ)
Contactor, 24 V 50 Hz, 3 pole, 380 V 400 V, 4 kW, Contacts N/C = Normally closed= 1 NC, Screw terminals, AC operation
Alternate Catalog No.
XTMC9A01U
Contactor, Application: Mini Contactors for Motors and Resistive Loads, DILEM contactors, Utilization category: AC1: Noninductive or slightly inductive loads, resistance furnaces, NAC3: Normal AC induction motors: starting, switch off during running, AC4: Normal AC induction motors: starting, plugging, reversing, inching, Connection technique: Screw terminals, Notes: Also suitable for motors with efficiency class IE3, Description: With auxiliary contact, Number of poles: 3 pole, Rated operational current AC3 380 V 400 V: Ie= 9 A, Rated operational current AC1 Conventional free air thermal current, 3 pole, 50  60 Hz Open at 40 °C: Ith =Ie= 22 A, enclosed: Ith= 16 A, Rated operational current AC1 Conventional free air thermal current, 1 pole open: Ith= 50 A, enclosed: Ith= 40 A, Max. rating for threephase motors, 50  60 Hz AC3 220 V 230 V: P= 2.2 kW, 380 V 400 V: P= 4 kW, 660 V 690 V: P= 4 kW, Max. rating for threephase motors, 50  60 Hz AC4 220 V 230 V: P= 1.5 kW, 380 V 400 V: P= 3 kW, 660 V 690 V: P= 3 kW, For use with: …DILE, Contacts N/C = Normally closed: 1 NC, Voltage AC/DC: AC operation
Delivery program
Product range
Contactors
Application
Mini Contactors for Motors and Resistive Loads
Subrange
DILEM contactors
Utilization category
AC1: Noninductive or slightly inductive loads, resistance furnaces
AC3/AC3e: Normal AC induction motors: Starting, switching off while running
AC4: Normal AC induction motors: starting, plugging, reversing, inching
AC3/AC3e: Normal AC induction motors: Starting, switching off while running
AC4: Normal AC induction motors: starting, plugging, reversing, inching
Notes
Also suitable for motors with efficiency class IE3.
Also tested according to AC3e.
Also tested according to AC3e.
Connection technique
Screw terminals
Description
With auxiliary contact
Number of poles
3 pole
Rated operational current
AC3380 V 400 V [I_{e}]
9 A
AC1Conventional free air thermal current, 3 pole, 50  60 HzOpenat 40 °C [I_{th }=I_{e}]
22 A
Max. rating for threephase motors, 50  60 Hz
AC3220 V 230 V [P]
2.2 kW
AC3380 V 400 V [P]
4 kW
AC3660 V 690 V [P]
4 kW
AC4220 V 230 V [P]
1.5 kW
AC4380 V 400 V [P]
3 kW
AC4660 V 690 V [P]
3 kW
Contacts
N/C = Normally closed
1 NC
For use with
…DILE
Actuating voltage
24 V 50 Hz
Voltage AC/DC
AC operation
Technical data
General
Standards
IEC/EN 60947, VDE 0660, CSA, UL
Lifespan, mechanical; Coil 50/60 Hz [Operations]
7 x 10^{6}
Lifespan, mechanical [Operations]
10 x 10^{6}
Maximum operating frequencyMechanical
9000 Ops./h
Maximum operating frequencyelectrical (Contactors without overload relay) [Operations/h]
Page 05/070
Climatic proofing
Damp heat, constant, to IEC 60068278
Damp heat, cyclic, to IEC 60068230
Damp heat, cyclic, to IEC 60068230
Ambient temperatureOpen
25  +50 °C
Ambient temperatureEnclosed
 25  40 °C
Ambient temperatureStorageMin. ambient temperature, storage
 40 °C
Ambient temperatureStorageAmbient temperature, storage max.
+ 80 °C
Mounting position
As required, except vertical with terminals A1/A2 at the bottom
Mechanical shock resistance (IEC/EN 60068227)Halfsinusoidal shock, 10 msBasic unit without auxiliary contact moduleMain contacts, make contacts
10 g
Mechanical shock resistance (IEC/EN 60068227)Halfsinusoidal shock, 10 msBasic unit without auxiliary contact moduleMain contacts Make/break contactsBreak contact
10 g
Mechanical shock resistance (IEC/EN 60068227)Halfsinusoidal shock, 10 msBasic unit with auxiliary contact moduleMain contacts make contactMake
10 g
Mechanical shock resistance (IEC/EN 60068227)Halfsinusoidal shock, 10 msBasic unit with auxiliary contact moduleAuxiliary contacts Make/break contacts
20/20 g
Degree of Protection
IP20
Protection against direct contact when actuated from front (EN 50274)
Finger and backofhand proof
Altitude
Max. 2000 m
Weight
0.17 kg
Terminal capacity of auxiliary and main contactsScrew terminalsSolid
1 x (0.75  2.5)
2 x (0.75  2.5) mm^{2}
2 x (0.75  2.5) mm^{2}
Terminal capacity of auxiliary and main contactsScrew terminalsFlexible with ferrule
1 x (0.75  1.5)
2 x (0.75  1.5) mm^{2}
2 x (0.75  1.5) mm^{2}
Terminal capacity of auxiliary and main contactsScrew terminalsSolid or stranded
18  14 AWG
Terminal capacity of auxiliary and main contactsScrew terminalsStripping length
8 mm
Terminal capacity of auxiliary and main contactsScrew terminalsTerminal screw
M3.5
Terminal capacity of auxiliary and main contactsScrew terminalsPozidriv screwdriver
2 Size
Terminal capacity of auxiliary and main contactsScrew terminalsStandard screwdriver
0.8 x 5.5
1 x 6 mm
1 x 6 mm
Terminal capacity of auxiliary and main contactsScrew terminalsMax. tightening torque
1.2 Nm
Main conducting paths
Rated impulse withstand voltage [U_{imp}]
6000 V AC
Overvoltage category/pollution degree
III/3
Rated insulation voltage [U_{i}]
690 V AC
Rated operational voltage [U_{e}]
690 V AC
Safe isolation to EN 61140between coil and contacts
300 V AC
Safe isolation to EN 61140between the contacts
300 V AC
Making capacity (cos ϕ to IEC/EN 60947)
110 A
Breaking capacity 220 V 230 V
90 A
Breaking capacity 380 V 400 V
90 A
Breaking capacity 500 V
64 A
Breaking capacity 660 V 690 V
42 A
Shortcircuit protection maximum fuseType ”2”, 500 V [gL/gG]
10 A
Shortcircuit protection maximum fuseType ”1”, 500 V [gL/gG]
20 A
AC
AC1Rated operational currentConventional free air thermal current, 3 pole, 50  60 HzOpenat 40 °C [I_{th }=I_{e}]
22 A
AC1Rated operational currentConventional free air thermal current, 3 pole, 50  60 HzOpenat 50 °C [I_{th }=I_{e}]
20 A
AC1Rated operational currentConventional free air thermal current, 3 pole, 50  60 HzOpenat 55 °C [I_{th }=I_{e}]
19 A
AC1Rated operational currentConventional free air thermal current, 3 pole, 50  60 Hzenclosed [I_{th}
]
16 A
AC1Rated operational currentConventional free air thermal current, 3 pole, 50  60 HzNotes
At maximum permissible ambient air temperature.
AC1Rated operational currentConventional free air thermal current, 1 poleNotes
At maximum permissible ambient air temperature.
AC1Rated operational currentConventional free air thermal current, 1 poleopen [I_{th}
]
50 A
AC1Rated operational currentConventional free air thermal current, 1 poleenclosed [I_{th}
]
40 A
AC3Rated operational currentOpen, 3pole: 50 – 60 HzNotes
At maximum permissible ambient temperature (open.)
Also tested according to AC3e.
Also tested according to AC3e.
AC3Rated operational currentOpen, 3pole: 50 – 60 Hz220 V 230 V [I_{e}]
9 A
AC3Rated operational currentOpen, 3pole: 50 – 60 Hz240 V [I_{e}]
9 A
AC3Rated operational currentOpen, 3pole: 50 – 60 Hz380 V 400 V [I_{e}]
9 A
AC3Rated operational currentOpen, 3pole: 50 – 60 Hz415 V [I_{e}]
9 A
AC3Rated operational currentOpen, 3pole: 50 – 60 Hz440V [I_{e}]
9 A
AC3Rated operational currentOpen, 3pole: 50 – 60 Hz500 V [I_{e}]
6.4 A
AC3Rated operational currentOpen, 3pole: 50 – 60 Hz660 V 690 V [I_{e}]
4.8 A
AC3Motor rating [P]220 V 230 V [P]
2.2 kW
AC3Motor rating [P]240V [P]
2.5 kW
AC3Motor rating [P]380 V 400 V [P]
4 kW
AC3Motor rating [P]415 V [P]
4.3 kW
AC3Motor rating [P]440 V [P]
4.6 kW
AC3Motor rating [P]500 V [P]
4 kW
AC3Motor rating [P]660 V 690 V [P]
4 kW
AC4Rated operational currentOpen, 3pole: 50 – 60 HzNotes
At maximum permissible ambient air temperature.
AC4Rated operational currentOpen, 3pole: 50 – 60 Hz220 V 230 V [I_{e}
]
6.6 A
AC4Rated operational currentOpen, 3pole: 50 – 60 Hz240 V [I_{e}
]
6.6 A
AC4Rated operational currentOpen, 3pole: 50 – 60 Hz380 V 400 V [I_{e}
]
6.6 A
AC4Rated operational currentOpen, 3pole: 50 – 60 Hz415 V [I_{e}
]
6.6 A
AC4Rated operational currentOpen, 3pole: 50 – 60 Hz440 V [I_{e}
]
6.6 A
AC4Rated operational currentOpen, 3pole: 50 – 60 Hz500 V [I_{e}
]
5 A
AC4Rated operational currentOpen, 3pole: 50 – 60 Hz660 V 690 V [I_{e}
]
3.4 A
AC4Motor rating [P]220 V 230 V [P]
1.5 kW
AC4Motor rating [P]240 V [P]
1.8 kW
AC4Motor rating [P]380 V 400 V [P]
3 kW
AC4Motor rating [P]415 V [P]
3.1 kW
AC4Motor rating [P]440 V [P]
3.3 kW
AC4Motor rating [P]500 V [P]
3 kW
AC4Motor rating [P]660 V 690 V [P]
3 kW
DC
Rated operational current openDC112 V [I_{e}
]
20 A
Rated operational current openDC124 V [I_{e}
]
20 A
Rated operational current openDC160 V [I_{e}
]
20 A
Rated operational current openDC1110 V [I_{e}
]
20 A
Rated operational current openDC1220 V [I_{e}
]
20 A
Magnet systems
Voltage toleranceAC operatedSinglevoltage coil 50 Hz and dualvoltage coil 50 Hz, 60 Hz [Pickup]
0.8  1.1 x U_{c}
Voltage toleranceAC operatedDualfrequency coil 50/60 Hz [Pickup]Voltage tolerance Dualfrequency coil 50/60 Hz, max. pickup voltage
1.1 x U_{c}
Power consumptionAC operationSinglevoltage coil 50 Hz and dualvoltage coil 50 Hz, 60 Hz [Pickup]
25 VA
Power consumptionAC operationSinglevoltage coil 50 Hz and dualvoltage coil 50 Hz, 60 Hz [Pickup]
22 W
Power consumptionAC operationSinglevoltage coil 50 Hz and dualvoltage coil 50 Hz, 60 Hz [Sealing]
4.6 VA
Power consumptionAC operationSinglevoltage coil 50 Hz and dualvoltage coil 50 Hz, 60 Hz [Sealing]
1.8 W
Duty factor
100 % DF
Switching times at 100 % U_{c}Make contactClosing delayClosing delay min.
14 ms
Switching times at 100 % U_{c}Make contactClosing delayClosing delay max.
21 ms
Switching times at 100 % U_{c}Make contactOpening delayOpening delay min.
8 ms
Switching times at 100 % U_{c}Make contactOpening delayOpening delay max.
18 ms
Switching times at 100 % U_{c}Make contactClosing delay with top mounting auxiliary contact
45 ms
Switching times at 100 % U_{c}Reversing contactorsChangeover time at 110 % U_{c}Changeover time min.
16 ms
Switching times at 100 % U_{c}Reversing contactorsChangeover time at 110 % U_{c}Changeover time max.
21 ms
Switching times at 100 % U_{c}Reversing contactorsArcing time at 690 V AC
12 ms
Current heat losses (3 or 4pole)
at I_{th}, 50 °C
5.9 W
at I_{e} to AC3/400 V
1.2 W
Impedance per pole
9.18 mΩ
Auxiliary contacts
Positive operating contacts to EN 6094751 appendix L, including auxiliary contact module
Yes
Rated impulse withstand voltage [U_{imp}
]
6000 V AC
Overvoltage category/pollution degree
III/3
Rated insulation voltage [U_{i}
]
690 V AC
Rated operational voltage [U_{e}
]
600 V AC
Safe isolation to EN 61140between coil and auxiliary contacts
300 V AC
Safe isolation to EN 61140between the auxiliary contacts
300 V AC
Rated operational currentAC15220 V 240 V [I_{e}]
6 A
Rated operational currentAC15380 V 415 V [I_{e}]
3 A
Rated operational currentAC15500 V [I_{e}]
1.5 A
Rated operational currentDC L/R ≦ 15 msContacts in series:1 [24 V]
2.5 A
Rated operational currentDC L/R ≦ 15 msContacts in series:2 [60 V]
2.5 A
Rated operational currentDC L/R ≦ 15 msContacts in series:3 [100 V]
1.5 A
Rated operational currentDC L/R ≦ 15 msContacts in series:3 [220 V]
0.5 A
Conv. thermal current [I_{th}]
10 A
Control circuit reliability [Failure rate]
<10^{8}, < one failure at 100 million operations
(at U_{e} = 24 V DC, U_{min} = 17 V, I_{min} = 5.4 mA) λ
(at U_{e} = 24 V DC, U_{min} = 17 V, I_{min} = 5.4 mA) λ
Component lifespan at U_{e} = 240 VAC15 [Operations]
0.2 x 10^{6}
Component lifespan at U_{e} = 240 VDC currentL/R = 50 ms: 2 contacts in series at I_{e} = 0.5 A [Operations]
0.15 x 10^{6}
Component lifespan at U_{e} = 240 VDC currentNotes
Switchon and switchoff conditions based on DC13, time constant as specified
Shortcircuit rating without weldingMaximum overcurrent protective deviceShortcircuit protection only
PKZM04
Shortcircuit rating without weldingShortcircuit protection maximum fuse500 V
6 A gG/gL
Shortcircuit rating without weldingShortcircuit protection maximum fuse500 V
10 A fast
Current heat loss at a load of I_{th} per contact
1.1 W
Rating data for approved types
Switching capacityMaximum motor ratingThreephase200 V
208 V
208 V
2 HP
Switching capacityMaximum motor ratingThreephase230 V
240 V
240 V
3 HP
Switching capacityMaximum motor ratingThreephase460 V
480 V
480 V
5 HP
Switching capacityMaximum motor ratingThreephase575 V
600 V
600 V
5 HP
Switching capacityMaximum motor ratingSinglephase115 V
120 V
120 V
0.5 HP
Switching capacityMaximum motor ratingSinglephase230 V
240 V
240 V
1.5 HP
Switching capacityGeneral use
15 A
Auxiliary contactsPilot DutyAC operated
A600
Auxiliary contactsPilot DutyDC operated
P300
Auxiliary contactsGeneral UseAC
600 V
Auxiliary contactsGeneral UseAC
10 A
Auxiliary contactsGeneral UseDC
250 V
Auxiliary contactsGeneral UseDC
0.5 A
Short Circuit Current RatingBasic RatingSCCR
5 kA
Short Circuit Current RatingBasic Ratingmax. Fuse
45 A
Design verification as per IEC/EN 61439
Technical data for design verification
Rated operational current for specified heat dissipation [I_{n}]
9 A
Heat dissipation per pole, currentdependent [P_{vid}]
0.4 W
Equipment heat dissipation, currentdependent [P_{vid}]
1.2 W
Static heat dissipation, noncurrentdependent [P_{vs}]
1.8 W
Heat dissipation capacity [P_{diss}]
0 W
Operating ambient temperature min.
25 °C
Operating ambient temperature max.
+50 °C
IEC/EN 61439 design verification
10.2 Strength of materials and parts10.2.2 Corrosion resistance
Meets the product standard's requirements.
10.2 Strength of materials and parts10.2.3.1 Verification of thermal stability of enclosures
Meets the product standard's requirements.
10.2 Strength of materials and parts10.2.3.2 Verification of resistance of insulating materials to normal heat
Meets the product standard's requirements.
10.2 Strength of materials and parts10.2.3.3 Verification of resistance of insulating materials to abnormal heat and fire due to internal electric effects
Meets the product standard's requirements.
10.2 Strength of materials and parts10.2.4 Resistance to ultraviolet (UV) radiation
Meets the product standard's requirements.
10.2 Strength of materials and parts10.2.5 Lifting
Does not apply, since the entire switchgear needs to be evaluated.
10.2 Strength of materials and parts10.2.6 Mechanical impact
Does not apply, since the entire switchgear needs to be evaluated.
10.2 Strength of materials and parts10.2.7 Inscriptions
Meets the product standard's requirements.
10.3 Degree of protection of ASSEMBLIES
Does not apply, since the entire switchgear needs to be evaluated.
10.4 Clearances and creepage distances
Meets the product standard's requirements.
10.5 Protection against electric shock
Does not apply, since the entire switchgear needs to be evaluated.
10.6 Incorporation of switching devices and components
Does not apply, since the entire switchgear needs to be evaluated.
10.7 Internal electrical circuits and connections
Is the panel builder's responsibility.
10.8 Connections for external conductors
Is the panel builder's responsibility.
10.9 Insulation properties10.9.2 Powerfrequency electric strength
Is the panel builder's responsibility.
10.9 Insulation properties10.9.3 Impulse withstand voltage
Is the panel builder's responsibility.
10.9 Insulation properties10.9.4 Testing of enclosures made of insulating material
Is the panel builder's responsibility.
10.10 Temperature rise
The panel builder is responsible for the temperature rise calculation. Eaton will provide heat dissipation data for the devices.
10.11 Shortcircuit rating
Is the panel builder's responsibility. The specifications for the switchgear must be observed.
10.12 Electromagnetic compatibility
Is the panel builder's responsibility. The specifications for the switchgear must be observed.
10.13 Mechanical function
The device meets the requirements, provided the information in the instruction leaflet (IL) is observed.
Technical data ETIM 8.0
Lowvoltage industrial components (EG000017) / Power contactor, AC switching (EC000066)
Electric engineering, automation, process control engineering / Lowvoltage switch technology / Contactor (LV) / Power contactor, AC switching (ecl@ss10.0.127371003 [AAB718015])
Rated control supply voltage Us at AC 50HZ
24  24 V
Rated control supply voltage Us at AC 60HZ
0  0 V
Rated control supply voltage Us at DC
0  0 V
Voltage type for actuating
AC
Rated operation current Ie at AC1, 400 V
22 A
Rated operation current Ie at AC3, 400 V
9 A
Rated operation power at AC3, 400 V
4 kW
Rated operation current Ie at AC4, 400 V
6.6 A
Rated operation power at AC4, 400 V
3 kW
Rated operation power NEMA
3.7 kW
Modular version
No
Number of auxiliary contacts as normally open contact
0
Number of auxiliary contacts as normally closed contact
1
Type of electrical connection of main circuit
Screw connection
Number of normally closed contacts as main contact
0
Number of normally open contacts as main contact
3

(Web)

Asset

Asset

Eaton EMEA DownloadCenter  download data for this item

Eaton EMEA DownloadCenter